NAVELEX EE 181-AA-OMI-110/E121 C-9412
Table 5-1. Maintenance Controls and Indicators
Light-emitting diodes (LED) illuminate to indicate the
first duress or intrusion alarm input.
Terminal Board A12
Display is reset by moving operating mode
switch to ACCESS OR TEST/RESET, then
back to SECURE.
Controls mode of operation for the delayed alarm output
(2-position toggle switch)
output at terminal S1-D as follows:
LATCH position - normal operating position. This per-
mits latched alarm conditions to remain until reset by
positioning operating mode switch to TEST/RESET.
NON-LATCH position - limits latched alarm output at
terminal S1-D to 10+2 seconds after alarm disappears.
When pressed, resynchronizes operation of Data Trans-
mitter and Data Receiver. Refer to TM 5-6350-264-14/
12 & P.
Power (2-position toggle
Connects ac power and emergency battery power to
Control Unit power supply.
Initiates alarm signal when CU door is opened. Pulling
switch plunger all the way out disables the switch.